Input Output Status Help

___________________________________________________________

This program should be used mainly to check status of input & output for VG108 system only, although it can also be used for simulation of program for a trained person.

VG108 has maximum 256 Inputs (Organized in 16 Inputs of one card, thus maximum 16 Input Cards) & maximum of 240 Outputs (Organized in 16 Outputs of one card, thus maximum 15 Output Cards).Screen is simulated as one card of 16 Input or Output.

Changing Card Number

Checking status of Input/Output of selected card

Changing status of Output(S) of selected card

Changing status of Input(S) of selected card

NOTE:

Untrained person should not use Send menu. To avoid above precaution one should change status only when VG108 unit power is turned on with emergency on (Input 0 is on) then only status should be changed except of Input 0.


Changing Card Number

__________________________________________________________________________

To increment card number you have to click on Next menu with help of the mouse.

To decrement card number you have to click on Back menu with the help of mouse.


Checking Status

__________________________________________________________________________

Clicking Get menu gets corresponding status of Input/Output from VG108 controller. If corresponding Input/Output is ON then Input/Output circle (simulated as card L.E.D) will turn to Green/Red (On Status) else it will turn to black (Off Status).This way one can see the status of all Input/Output.


To change Output Status

__________________________________________________________________________

To change status of Output(S), one must set remote control to YES in Plant setting.

If one wants to test output(S) then it is advised that one should change when power is turned on with Emergency(Input 0) is on.

First click Get menu. This action gets corresponding status of Output from VG108 controller and also enables Send menu. If Output is on then its L.E.D turns to red else turns to black. To change Output status of selected card one has to click Output(S) NAME, then click Send menu. This action will set selected card Outputs into the controller.

Output 0 & Output 7 status may not change as they are used by system software. Similarly other output may not change their status if they are related to different program.


To Change Input Status

__________________________________________________________________________

To change status of Input(S), one must set remote control to YES in Plantsetting and required Input should have been set for remote on.

First click Get menu. This action gets corresponding status of Input from VG108 controller and also enables Send menu. If Input is on then its L.E.D turns to green else turns to black. To change Input status of selected card one has to click Input(S) NAME, then click Send menu. This action will set selected card Inputs into the controller.

Remember if a particular program is written for an Input X, this program may be activated on changing status of that Input X and this may change status of related output also. This way one can simulate remote function.